Solar 10 KW, USGS Gri-Tie Solar System is pre-engineered with the highest quality Canadian Solar 295 Watt Monocrystalline solar panels, Fronius Primo 10KW inverter, Solar USMR Mounting Hardware.This offers greater design flexibility and simplified installation, accommodating different roof planes, pitches, or rooftop obstacles.This USGS Gri-Tie Solar System is relatively simple to layout and install. We have provided all of the main parts you will need for your grid tie package. Building and installing your own home solar system is not only the smart choice for controlling your expenses, it may be on the most satisfying DIY projects you ever have undertaken.
NOTE: The quotes, the material can be individually costumed for a specific situation and customer needs
NOTE: Solar design services for a roof mount residential project will be absolutely free of charge ( Email for more details )
System Size : 10,620 Watts
Monthly kWh @ 6 Sun Hours Per Day *STC : 980 kWH
Panel & Inverter Warranty : 25 Years
||Canadian Solar 295W Monocrystalline Module. 5BB, 60 cell
||Fronius Primo 5.0 Inverter, transformerless, single phase, integrated Wi-Fi and Sunspec Modbus interface for seamless monitoring and datalogging.
||Fronius Rapid Shutdown – multi item – for systems up to 600V
||Solar Complete Roof Mounting Hardware
| AC 1.00 Disconnect-30A
||Square D AC Disconnect, NEMA 3R, 30A, 240 VAC, 2-Pole Unfused
||10 oz M-1 Structural Sealant part no. F1270- While, Squeeze Tubes
|| 12 pcs
NOTE / DO – IT – YOURSELF INSTALLATION
It is the responsibility of the purchaser to ensure that all products are installed and operated in accordance with local and national building codes as specific by the NEC (National Electric Code), UBC (Uniform Building Code) or IBC (International Building Code) and local utility company policy. These codes may vary from city to city and county to county. All Grid-tied solar installations should be permitted and inspected, where required, by the local inspection authority in the same manner as other equivalent electrical systems. It is always a good idea to contract with a local licensed electrician to at least do the final electrical connection of your Solar 5 KW, USGS Grid-Tie Solar System from the AC disconnect to your home utility breaker box. Some local permitting authorities require that a licensed electrician do all the wiring from the rack to the utility interconnect.
Perform all electrical installations in accordance with all applicable local electrical codes and the National Electrical Code (NEC), ANSI/NFPA 70. Be aware that only qualified personnel should install or replace Enphase MicroInverter. Do not attempt to repair the Enphase MicroInverter as it contains no user-serviceable parts. If it fails, please contact Enphase customer service to obtain an RMA (return merchandise authorization) number and start the replacement process. Tampering with or opening the Enphase MicroInverter will void the warranty. Before installing or using the Solar 10KW, USGS Grid-Tie Solar System please read all instructions and cautionary markings in the technical description. Connect the Microinverter to the utility grid only after receiving prior approval from the electrical utility company. Be aware that the body of the microinverter is the heat sink. Under normal operating conditions, the temperature is 15°C above ambient, but under extreme conditions the microinverter can reach a temperature of 80°C. To reduce risk of burns, use caution when working with microinverter. Do NOT disconnect the solar panel from the Fronius Primo Inverter without first removing AC power.